13113.7. (a) (1) Except as otherwise provided in this section, smoke alarms, approved and listed by the State Fire Marshal pursuant to Section 13114 at the time of installation, shall be installed, in accordance with the manufacturer s instructions in each dwelling intended for human occupancy.
(2) For all dwelling units intended for human occupancy for which a building permit is issued on or after January 1, 2014, for alterations, repairs, or additions exceeding one thousand dollars ($1,000), the permit issuer shall not sign off on the completion of work until the permittee demonstrates that all smoke alarms required for the dwelling unit are devices approved and listed by the State Fire Marshal pursuant to Section 13114.
(3) However, if any local rule, regulation, or ordinance, adopted prior to January 1, 1987, requires installation in a dwelling unit intended for human occupancy of smoke alarms which receive their power from the electrical system of the building and requires compliance with the local rule, regulation, or ordinance at a date subsequent to the dates specified in this section, the compliance date specified in the rule, regulation, or ordinance shall, but only with respect to the dwelling units specified in this section, take precedence over the date specified in this section.
(4) Unless prohibited by local rules, regulations, or ordinances, a battery-operated smoke alarm, which otherwise met the standards adopted pursuant to Section 13114 for smoke alarms at the time of installation, satisfies the requirements of this section.
(5) A fire alarm system with smoke detectors installed in accordance with the State Fire Marshal s regulations may be installed in lieu of smoke alarms required pursuant to paragraph (1) or (2) of this subdivision, or paragraph (3) of subdivision (d).
(b) Dwelling units intended for human occupancy, as used in this section, includes a one- or two-unit dwelling, lodging house, apartment complex, hotel, motel, condominium, stock cooperative, time-share project, or dwelling unit of a multiple-unit dwelling complex, or factory-built housing as defined in Section 19971. For the purpose of this part, dwelling units intended for human occupancy does not include manufactured homes as defined in Section 18007, mobilehomes as defined in Section 18008, and commercial coaches as defined in Section 18001.8.
(c) A high-rise structure, as defined in subdivision (b) of Section 13210 and regulated by Chapter 3 (commencing with Section 13210), and which is used for purposes other than as dwelling units intended for human occupancy, is exempt from the requirements of this section.
(d) (1) The owner shall be responsible for testing and maintaining alarms in hotels, motels, lodging houses, apartment complexes, and other multiple-dwelling complexes in which units are neither rented nor leased.
(2) The owner of a hotel, motel, lodging house, apartment complex, or other multiple-dwelling complex in which units are rented or leased, and commencing January 1, 2014, the owner of a single-family dwelling that is rented or leased, shall be responsible for testing and maintaining alarms required by this section as follows:
(A) An owner or the owner s agent may enter any dwelling unit, efficiency dwelling unit, guest room, and suite owned by the owner for the purpose of installing, repairing, testing, and maintaining single station smoke alarms required by this section. Except in cases of emergency, the owner or owner s agent shall give the tenants of each such unit, room, or suite reasonable notice in writing of the intention to enter and shall enter only during normal business hours. Twenty-four hours shall be presumed to be reasonable notice in absence of evidence to the contrary.
(B) At the time that a new tenancy is created, the owner shall ensure that smoke alarms are operable. The tenant shall be responsible for notifying the manager or owner if the tenant becomes aware of an inoperable smoke alarm within his or her unit. The owner or authorized agent shall correct any reported deficiencies in the smoke alarm and shall not be in violation of this section for a deficient smoke alarm when he or she has not received notice of the deficiency.
(3) On or before January 1, 2016, the owner of a dwelling unit intended for human occupancy in which one or more units is rented or leased shall install additional smoke alarms, as needed, to ensure that smoke alarms are located in compliance with current building standards. Existing alarms need not be replaced unless the alarm is inoperable. New smoke alarms installed in compliance with current building standards may be battery operated provided the alarms have been approved by the State Fire Marshal for sale in the state. This paragraph shall not apply to fire alarm systems with smoke detectors, fire alarm devices that connect to a panel, or other devices that use a low-power radio frequency wireless communication signal.
(e) A violation of this section is an infraction punishable by a maximum fine of two hundred dollars ($200) for each offense.
(f) This section shall not affect any rights which the parties may have under any other provision of law because of the presence or absence of a smoke alarm.
(Amended by Stats. 2012, Ch. 420, Sec. 1. Effective January 1, 2013.)Section: Previous 13111.3 13112 13112.1 13112.2 13113 13113.5 13113.6 13113.7 13113.8 13113.9 13113.95 13114 13114.1 13114.2 13114.3 Next
Last modified: September 9, 2016